7 ACH at 50Pa. The thermal envelope must be verified even when using the perscriptive method
Space Heating System
At least one thermostat shall be provided for each separate heating and cooling system.
Lighting systems must have controls specific to the building's layout and additional controls allowing occupants to reduce the lighting load and override any automatic time switch controls.
Daylight zones have specific lighting control requirements.
Interior lighting power allowances are specific to building type
All exterior building grounds' luminaries operating at > 100 watts must have a minimum efficacy of 60 lumens per watt unless controlled by motion sensors or is exempt.
Pools deriving >60% heating energy from site-recovered or solar energy are excempt from pool specific energy saving measures